刘易斯 - 纽卡斯尔, OK
科里 - 纽卡斯尔, OK
达里尔 - 纽卡斯尔, OK
这是顶级的暖气 & 我用了好几年的航空公司. They are always there at designated time and the technicians are very knowledgeable and professional. 和这些人在一起是不会出错的.
出来要求停止加热. 上次我出去的时候系统里有条线松了. 循环加热，一切正常.
出来叫唤 for a system not cooling and the thermostat was blank. Customer stated that he put new batteries in the thermostat and the thermostat was no longer blank but the system still wasnâ€™t working. Customer was concerned that we may have done something since we were out to do the maintenance a week or so ago. I checked system over and found unit to have proper power but the door switch to be faulty and the wires were burned. Asked customer about any possible power surges since weâ€™ve been out and they said they might have had one. I told customer I could replace the switch, and just bypass it for now. 顾客让我绕过开关. Iâ€™ll look into getting a replacement in the mean time and schedule a time to come back out.
我是为一个银会员而来的秋季调音. I spoke with the homeowner and found that the ac system is running well. I then replaced the filters that the homeowner provided and inspected the duct and furnace. I found the furnace to be running properly and the 蒸发器线圈 to be clean. 我现在没有发现系统有问题.
站出来说系统没有正常冷却. 我们6月出去找泄密者. I was able to locate one and repair a small leak by the inlet on the suction line of the 蒸发器线圈. 客户说直到这周它都工作得很好. 我检查了系统，发现制冷剂又少了. 是不是又发现了另一个漏洞. It is located at the bottom right corner of the 蒸发器线圈 where it is severely rusted. 这是一个无法修复的地方. I made homeowner aware of the condition of the coil last time I was out, 蒸发器盘管只有5年的标准保修期, 它是2015年安装的. 为客户提供更换蒸发器盘管的价格. Customer wanted to charge system for now and plane for replacement at a later date. 增加2磅的410a系统得到适当的过冷9.
2021年6月24日杰森B来到这里进行春季调整. 与房主谈论系统性能. 在恒温器上启动循环系统. Inspected coil, blower cabinet, 电动机, float switch and all 电器元件. Verified pressures, capacitor, contactors, hard start, fan and compressor amps. 清洗后的冷凝器盘管和循环系统重新启动. 此时系统运行正常.
站出来说系统没有正常冷却. Customer stated they had a company out a few weeks ago and they added refrigerant to the system. 现在系统也在做同样的事情. 顾客被告知一些关于线圈的事情. 想听听别人的意见. 我检查了系统，发现它被冻结了. 我告诉顾客我今天晚些时候再来, 让他们在我回来之前不要再做了. 我暂时打开鼓风机使空气流通. 回来呼叫检查系统. 发现beplay2网址制冷剂又低了. 客户想让我做一个漏洞搜索来找到可能的漏洞. 进行泄漏搜索，发现蒸发器盘管有针孔泄漏. 让客户知道我发现了什么. Customer wanted me to look up the warranty information tomorrow on the coil and see if it may still be under warranty so they can replace it in the near future. 我添加了2磅的410a系统得到适当的充电系统. 交流电正在正常冷却.
为客户进行beplay2网址系统的预防性维护. 客户最近更换了过滤器，不久将再次更换. 我检查了鼓风机总成, 电动机, 电器元件, 蒸发器线圈, 阁楼的排水和设备的总体状况. 彻底清洁冷凝器盘管. Inspected the capacitor, contactor, hard start kit, compressor, and fan 电动机. 风扇电机轴有一点弹性, 但仍然操作, 让房主意识到它可能开始走出去. Existing hard start kit was also falling apart and needed to be replaced. Brought it up to the customer and recommended replacement as the existing one is no longer operating. 客户批准的替代. I replaced the hard start kit in AC, then checked amps, temperatures and pressures of condenser. System is cooling properly within manufactured specifications 在这 time.
I arrived to bid 3 bays for new duct work and connecting them to the package units. 每个房间将有8个补给点和1个本地返回. They will set there own package units we will run the duct from the package unit to the grills. 烤架为圆形烤架. If you support the material we will charge time and material needed to complete the job for a team of 3 installers to complete the job on all 3 bays. 没有零件保修. 工匠船只有一年的保修期.
为客户估计更换冷凝器线圈, 或更换所有3个系统的交流机组和蒸发器盘管. Which includes estimates for two 3 ton units that supply downstairs and one 1 1/2 ton system that supplies upstairs.
出来叫了冷凝器上的估价, but customer also wanted to know about combing out the condenser coil that was damaged by hail. Due to age and condition of coil, combing the fins is only causing more damage on most of the coil. Fins will tear if the coil is combed completely, and in some cases the damage canâ€™t be combed out. 将得到冷凝器盘管的定价和可用性. 由于使用年限的关系，可能无法提供精确的线圈. 我找到了交流系统的替换线圈. 我在这个估算中包含了2个估算. 一个替换现有的线圈，一个替换交流电和线圈
出来找炉子取暖不正常. Customer stated that the system wasnâ€™t heating and blowing cool air. I checked system over and found that the furnace is a 90% furnace and that the condensation line for the furnace was frozen solid. I recommended customer putting a space heater in the attic to help it thaw. 我安装了临时排水管道让系统暂时运转. 我们需要在下周的某个时候来重新接上排水管. I also suggested heat wrap on the condensation line to keep it from freezing. 回来把暖气冷凝排水孔装回去. 排水管道已经解冻，可以再次使用. 我重新连接排水管到炉子和循环加热器. 炉子排水正常. 我把管子用绝缘材料包了起来. I still suggested heat wrap to keep this from happening in the future.
用两层楼和两个清洗鸭子的系统检查家, 空气中和尼古丁烟雾, 以及其他空气质量问题. 客户也有兴趣谈谈恒温器的更换. Looked over both systems, ductwork, ductwork composition and air quality options. The major issue with the downstairs system is that the old mylar return that has deteriorated to the point of letting in attic air. 建议更换管道系统, this involves moving the flu pipe for the furnace and the hot water tank in the garage and building a custom Plenum to attach to. Also talked about blowing in the attic insulation and remediating home with hydroxyl treatment for three days. 客户将在未来的某一天查看恒温器的选择. 对霍尼韦尔和nest可编程产品感兴趣. Customer will also look into having air ducts cleaned at a future date.
执行蓝盾防护方案beplay2网址维护. 改变过滤器. 清洗冷凝器. 测试电容和电机放大器的拉力. 压缩放大器在范围内. 制冷剂水平在范围内. 此时系统正在冷却.
银俱乐部加热调整2013承运人80%的熔炉. 询问顾客热点和冷点, how temperatures are keeping up and if they had turned on the furnace yet this season. 检查过滤器，它们需要在10月份更换. 首页 is heating and cooling well and furnace has not been turned on yet. 打开炉膛检修面板，清洗火焰传感器. 循环系统在热模式下进行系统预检查. 循环系统关闭并测试鼓风机电容器. 拆下鼓风机，检查叶轮和热交换器. 检查烟道. 检查了蒸发器盘管和供应管道系统. 检查了回程管道系统，需要清洗一下. Cycled system on and checked hot surface igniter, blower amps and inducer amps. 鼓风机轮在运行范围内，但运行速度有点高.4安培, The returns are slightly undersized for the system and the filters are 2/3 used, 这可能是原因. 测试气体压力并复位气体塞. 检查了温升和室内增量t. 系统加热正常!在这
出来叫唤. 客户声明AC wasnâ€™t冷却正确. 我检查了系统，发现电容器坏了. 我和客户讨论了客户的维修需求和定价. 电容器在保修期内，但劳动isnâ€™t. 我更换了电容器和循环系统上. 我发现beplay2网址的制冷剂不足. 系统运行在4度过冷，它需要10度. 我添加了1.6磅的410a来获得适当的过冷. 此时系统正在正常冷却. I recommended customer replace coil in attic seeing there could be a possible leak in it.
测试电容和电机放大器的拉力, 压缩机amp画, 制冷剂等级达到2005协和beplay2网址
2007 好man Air Conditioner and 2013 RUUD Furnace summer preventative maintenance plan.
Cleaned system and tested all components to American standard air conditioner